22.214.171.124 Method for API Gravity Testing
Collect approximately two volumes--100 milliliters (3.4 ounces) of fuel
sample. Balance the sample to a prescribed temperature (for example, 15°C or
47°F) and transfer the sample to a cylinder prepared at approximately the same
Select an appropriate hydrometer and lower it into the cylinder. Allow the
hydrometer to settle. After temperature equilibrium is attained (approximately 5
minutes), take a temperature reading from the hydrometer scale and record it
according to site procedure.
All parts and tools referred to in the following steps can be identified in
Figure 1.1, page 1-5, or on the test kit placard (see Loading Plan).
2.4.2 Installing the Quick-Release Valve
Follow the procedure for installing the quick-release valve as described in
Section 2.3.2. Refer to Figure 2.1.
Make sure that the pressure in system does not exceed 100 psi.
2.4.3 Assembling the Sampler Valve Hose Assembly
Follow the procedure for assembling the sampler valve hose assembly as
described in Section 2.3.4. Refer to Figure 2.5.
Do not over-tighten or damage to the monitor or membrane might occur.
2.4.4 Attaching the
Screw the PVC
PVC Sample Bottle to the Remote Sampling
sample bottle mouth onto the remote sampling assembly