5-7. REMOVE/INSTALL SURGE TANK - Continued.
Install Surge Tank. (Figure 5-3).
Apply teflon tape to male fittings. Be sure to wrap teflon tape in same direction of pipe
Install pipe and union fitting to surge tank.
Position surge tank into storage cabinet and connect union joint.
Tighten union joint.
The surge tank must have 20 psi before operation.
Close water faucet.
Close circuit breaker CB16 located in the panelboard assemble.
Turn the WATER PUMP switch to the ON position.
Check for leaks and verify proper operations. (Refer to operating procedures contained
in paragraph 2- 12.b.)