4-26. RE4MOVE/INSTALL CONTROL UNIT 9,000 BTU - continued.
Attach the temperature selector switch sensing bulb into the temperature selector
switch mount located on top of evaporator coil.
Install bulb clamp screws and two lockwashers.
Align the plenum assembly to the plenum mount plate and install eight plenum
Replace packing compound around the plenum and capillary tubing.
Connect the ECU main input cable.
Push in remote plug and tighten hex head of rod connector.
Close appropriate circuit breaker and verify proper operations.