Table 4-1. Unit Preventive Maintenance Checks and Services - continued
ITEM TO BE INSPECTED
PROCEDURE: CHECK FOR AND HAVE REPAIRED,
FILLED OR ADJUSTED AS NEEDED
WATER SYSTEM - continued
g. Check drain tubing, piping, valves and hose connections for good
condition. No physical damage. No leaks.
h. Check demineralize cartridges for good water flow (10 gpm). No
GAS ALARM SYSTEM
Check gas alarm control unit and gas detector for good condition and
proper operation. No physical damage. No missing or loose mounting
hardware or fasteners. No broken or loose electrical connections. Refer
to TM 10-6665-297-13&P for further PMCS instructions.